Boiler Repairs in Sandbach
One-off boiler repair
Call now for a quote
- A boiler repair carried out by one of our local Gas Safe® boiler breakdown engineers
- Fully transparent upfront charging system
- All boiler makes and models repaired
- 12 months’ guarantee on parts and labour
Fixed Fee £95
- A discounted boiler repair for a fixed fee, includes a single part, and all labour required to fit that part
- A free annual boiler service
- Ongoing care for your boiler and central heating system
- Unlimited claims
- Nothing to pay per future repair
- Includes all parts and labour
Are You Looking for Boiler Repairs in Sandbach?
No matter what type, make or model of boiler you have in your home, property, or place of work, YourRepair Plumbers can quickly diagnose and repair your boiler using only high-quality components and parts.
We specialise in boiler repairs in Sandbach, so unlike some plumbers, we will never tell you to replace your boiler unless it is definitely more cost effective to do so. If we think a new boiler could save you money, we will let you know, but we won’t make that decision for you.
Why Choose YourRepair for Boiler Repairs in Sandbach?
- 12 month guarantee on all our work
- All our rates are 100% transparent
- Boiler diagnostic and safety checks, to quickly identify the problem
- Fast reliable response
- All our staff are CRB (DBS) checked
- Friendly, uniformed staff, with visible identification
Read below for some examples of boiler repairs in Sandbach that YourRepair have completed recently:
What the problem was:
Alpha condensing combi boiler with an intermittent fault, when the temperature drops the boiler trips the electrics. Had British Gas out about six months ago who couldn’t find anything wrong with the system. But problem is now getting worse now the cold weather has come.
What we did:
The job was booked in for a time slot that was convenient with the customer. A pre-authorisation of the customer’s credit card was taken on our secure PCI regulated system, for our customers security.
Although all our gas engineers have vast experience in boiler breakdown, in fault finding problems such as this, our Call Advisors will always send one of our more senior engineers to save the customer time and money.
Our engineer found the fault to be the flue and is a common mistake to make with Alpha boilers. Most boilers require the flue to be angled slightly upwards or horizontally, however, Alpha boiler are slightly different, it is recommended that the flue be angled slightly downwards. On this boiler, the flue was angled slightly upwards, and this was causing the condensation that developed on cold days to drip onto the thermostat.
A second visit was organised, and confirmed in writing via our Call Agent, to re-adjust the flue, and fit a new thermostat, that had water damage.
This seem to of rectified the problem, but as the fault is intermittent, customer is aware to call us, should the problem re-occur.
Fault found by experienced heating engineer and problem rectified.
Where the big boys had failed, YourRepair did a very good job, quickly and efficiently.
What the problem was:
Customer put the heating on for the first time after the summer and upstairs radiators are heating up as normal, but downstairs radiators are cold.
What we provided:
Customer was at work all week, and couldn’t arrange time off, so we gave him the option of either an early evening appointment, or a Saturday booking. Customer opted for a Saturday booking, at no additional cost. The YourRepair Call Advisor checked the online diary management system to arrange the first available appointment slot.
The engineer arrived on Saturday morning in full YourRepair uniform carrying ID to confirm where he was from. He suspected that it wasn’t a fault with the boiler, but a blockage in the system.
To test this, he turned of all the radiators upstairs, and and then the radiators started warming up downstairs. As they did, he turned each one off, until the final radiator was getting warm, this was then bled.
When the engineer then turned the radiators back on, the heat was evenly spread throughout the house. He checked the boiler whilst he was at the property to ensure this was working correctly.
Work was completed in under one hour.
Blockage removed from radiator, and heat being distributed evenly through the system.
Your Repair did an excellent job, they did exactly what was agreed, and left my property clean. The engineer was very well mannered and professional.